|Description||Type 2 surge arrester for power lines|
|IEC category / EN type||II , T2 / T2|
|Number of ports||1|
|Nominal voltage UN AC||240/415 VAC (TN-S) / 240/415 V AC (TT)|
|Maximum continuous operating voltage UC - L-N / N-PE||335 V AC / 260 V AC|
|Residual current IPE||≤ 5 μA|
|Short-circuit current rating ISCCR||25 kA|
|Follow current interrupt rating Ifi - N-PE||100 A (260 V)|
|Max. discharge surge current Imax (8/20)μs - L-N / N-PE||40 kA / 40 kA|
|Voltage protection level UP L-N / N-PE||≤ 1,5 kV / 1,5 kV|
|Nominal discharge surge current In (8/20)μs - L-N / N-PE||20 kA / 20 kA|
|Max. required backup fuse with branch wiring||125 A AC (gG)|
|Max. required backup fuse with V-type through wiring||80 A AC (gG)|
|Ambient temperature (operation)||-40 °C ... 80 °C|
|Permissible humidity (operation)||5 % ... 95 %|
|Degree of protection||IP 20|
SHIPPING AND EXPORT INFORMATION
|GROSS WEIGHT kg||0.105|
|CN (Combined Nomenclature)||85363030|
SENECA offices will be closed from 23 December to 7 January included. Business activities will resume regularly on Monday 8 January. To guarantee you a punctual shipment of products by Thursday 21 December (last day of shipping), we kindly ask you to send any requests no later than Wednesday 20 December. Orders received from December 21st will be dispatched from January 8th.
While thanking you for your cooperation, we wish you a happy winter holidays!
SPD 230VAC, no FM contact, tipe 2 with 3 conductors?
Replacement plug 1 LN / PE S400HV-2, no contact FMII / T2 335Vac / 260Vac?
Replacement plug N / per S400HV2 II / T2 335 VAC / 260 VAC / -335 Vac / 260Vac?